The FMM1 mounts directly to 4 square electrical boxes switch with thumb in the direction shown in Figure 1. INSTALLATION AND MAINTENANCE INSTRUCTIONS Figure 3. Typical 2wire initiating circuit configuration, NFPA Style B: M500M420 420mA Analog Input Module BEFORE INSTALLING This information is included as a quick reference installation guide. Refer to the con trol panel installation manual Removing Rotary Switch Stop: 9 NOTICE: This manual should be left with the owneruser of this equipment.
8 7 6 General Description The FMM1 Monitor Module is intended for use in intelligent, twowire systems, where the individual address of each module is selected using the builtin rotary switches.
FRM1 Relay Control Module INSTALLATION AND MAINTENANCE INSTRUCTIONS Before Installing Refer to the appropriate Notifier control panel installation manual for detailed system information.
If the modules will be installed in an existing operational system, inform the operator Analog Addressable Manual Pull Stations.
1. 0 Description. These instructions cover the installation of the FMM325A (Single Action) and FMM325AD (Dual Action) Analog Addressable Manual Pull Station kits in an analog system controlled by Bosch FPA1000 Analog Addressable Fire FZM1 Interface Module BeFore InstallIng This information is included as a quick reference installation guide.
Refer to the control panel installation manual for detailed system information. EN Installation Instructions Multiplex Addressable Manual Pull Stations FMM7045, FMM7045D Installation The FMM1 module mounts directly to a standard 4 in. square, 2. 124 in. (54 mm) deep, electrical box. Mounting hardware and installation instructions are provided with each module.
All wiring must conform to applicable local codes, ordinances, and regulations. These modules are